As a necessary safety facility in the current community, the combustible gas alarm detector is also well received in the detection of flammable gas. It has gradually become an essential security device for every household. Then we usually need to avoid any misunderstandings when installing flammable gas detectors!
What are the misunderstandings of the combustible gas detector installation: the undesired installation location
Firstly, avoid installing in places with high environmental impact, such as places with high wind flow rate such as passages, places with water mist or dripping water, places near the stove that are easily polluted by oil smoke, steam, etc. or high temperature environment (such as directly above the stove). Or a place that is obscured by other objects (such as inside a cabinet).
What are the misunderstandings of the combustible gas detector installation: installation distance
Installed on an indoor wall that is within 4 meters of the gas appliance or gas source and 2 meters away. And according to the type of gas detected, select the upper and lower positions of the installation:
Liquefied petroleum gas: within 0.3 meters from the ground.
Artificial gas, natural gas: within 0.3 meters from the ceiling.
What are the misunderstandings of flammable gas detector installation: correct installation method
1. At the selected wall position, make the punching mark corresponding to the two mounting holes on the random mounting plate (the hook on the board should be horizontally upward).
2. lay the mounting holes, put the rubber plugs in random, and then fix the mounting plate to the wall with random self-tapping screws.
3. Align the three holes on the back of the machine with the fixing hooks on the mounting plate and hang the body.
4. Connect the relevant output signal line and turn on the power.
What are the misunderstandings of the combustible gas detector installation: learn to check the working status
Normal monitoring status: power on preheating, green light is steady after 3 minutes, indicating that the alarm is working normally in the monitoring state.
During the preheating process, the alarm red, yellow and green three-color lights flash, and it is normal to disappear before the green light is on.
Self-test status: Press the “Self-test” button, the three-color light flashes, and the alarm sounds “beep…beep…” until the green light is on, and the alarm starts to work stably.
On-site alarm status: When the alarm detects that there is gas, it will flash red. When the gas concentration reaches the alarm point, the alarm will emit a “beep…beep…” intermittent squeaking, and the red indicator will flash to remind the user to do so as soon as possible. On-site processing.
What are the misunderstandings of the combustible gas detector installation: alarm emergency treatment
Do not turn on the light or turn on any electrical switch when the detector is alarmed by gas leakage and use the automatic cut-off device; immediately open the window for ventilation, and wait for the red alarm indicator of the detector to go out, find the cause of the gas leak (cannot When confirming the cause, you should contact the relevant gas company for processing) and eliminate it.
Confirm that the detector does not continue to alarm (the gas does not continue to leak), press the manual switch to turn on the automatic cut-off device to recover the gas.
The use of gas leak alarms greatly reduces the probability of major accidents due to gas leaks in locations where gas appliances are used. It is also hoped that everyone can pay attention to the installation position and distance when installing the combustible gas alarm detector to ensure that the gas detector can work normally.
Focus on security technology innovation and lead the development of AI industry. The 17th China I...
On May 11, 2019, our company Yaoertai was founded 14th anniversary! In the past 14 years, we hav...
Saturday, the first week of work in 2019, On a sunny afternoon, Yaoertai, all business colleagues...
The 28th China (Beijing) International Building Decoration and Materials Expo will be held on Mar...
The 15th R + T Asia Shanghai Door and Window Sunshade Exhibition will be held from February 27th ...
The frequency used by the radio remote control is 433Mhz or 315Mhz, also referred to as 433 remot...
The infrared alarm can detect the infrared rays emitted by the human body, and is composed of an ...
Congratulation YET Global Sources Electronics Exhibition bring to a successful close Gate remote ...